|Product Name:||Industrial Cabinet Air Conditioner R134a AC220V Door Mounted||Application:||Telecommunication|
|Cooling Capacity:||3000w||Rated Power:||1240w|
|Power Supply:||220V AC/48V DC||Working Temperature:||-40 ℃ - 55 ℃|
|Mounting:||Door Mounted/Side Mounted||Certificate:||CE CCC|
|After Warranty Service:||Video Technical Support, Online Support||Warranty:||1 Year|
Cabinet Air Conditioner R134a,
AC220V Cabinet Air Conditioner,
Telecom Outdoor Cabinet Air Conditioner
Industrial Cabinet Air Conditioner R134a AC220V Door Mounted
1. Industrial Cabinet Air Conditioner Introduction
Industrial cabinet air conditioner is one kind of refrigeration product self-developed for cabinet. It is applicable in the place where the cabinet internal heat is very large, the internal electronic equipment is sensitive to the environment temperature and which should be isolated internally and externally completely. This product has multiple functions, high reliability, and has the feature that it can start to work without complex debugging after powering.
2. Industrial Cabinet Air Conditioner Data Sheet
|Circuit max pressure||26bar|
3. Industrial Cabinet Air Conditioner Features
1)Good design, stable structure and easy maintenance.
2)Widely used for outdoor telecommunication cabinets, battery cabinets, electric cabinets and industry control cabinets etc.
3)Door mounted, side mounted and top mounted available.
4)The protective level is IP55, can protect cabinet from moisture, dust and water. It can be installed indoor and outdoor, run at high ambient temperature of 55℃.
5)Digital temperature controller and high precision of temperature control.
6)CE certified, which can meet EU RoHS requirements.
4. Application of Industrial Cabinet Air Conditioner
Cabinet air conditioner is widely used in outdoor communication cabinet, electrical cabinet, industrial cabinet and other occasions need heat dissipation. Create a cool, dry and safe environment for the operation of equipment and electrical enclosure.
5. Industrial Cabinet Air Conditioner Details
6. Cooling system
6.1 Basic Components
Cabinet air conditioner is composed of compressor, condenser, evaporator, electric control system, expansion valve and capillary tube, dry filter and fans etc.
6.2 Cooling Theory
The compressor takes in the gas refrigerant from the evaporator and compresses it into high temperature and high pressure then sends it into the condenser. The refrigerant will release heating in the condenser and then the cold high pressure liquid goes through capillary throttling and turns into low temperature and low pressure and then flows in to the evaporator. The refrigerant will absorb heat and then turns into gas in the evaporator. Thus forms the cooling cycle system.
The condenser and evaporator has circulation fan to enhance air convection and heat exchange efficiency. The heat exchange between condenser and air is outside the control box and that of evaporator and air is inside the control box.
The electrical system is mainly monitoring the temperature of the cooled closed cabinet and controls the cooling circulation by setting temperature.
6.3 Drawing of cooling theory